This is a thread to ask NEC code related questions.
Example16: What is the ampacityto size the feeder conductor if it supplies the following two motors?
1.One 7.5-hp, 230V, single-phase motor
2.One 5-hp, 230V, single-phase motor
Ans: Table 430.248 gives 40 A and 28 A as individual FLC of...